Inactivation of the waste water coming from the autopsy roomRef.: 3800/EU
INACTIVATION OF WASTE WATER COMING FROM THE AUTOPSY: Réf.3800 / EU. All the effluents, from the room of autopsy, the liquid discharges risk to be contaminated, and must be necessarily treated.
These discharges are loaded in organic matters, and in simple chemicals, they pour directly by gravity in the tank buffer.
The operated process will be chemical under the principle of the inactivation of microorganisms under the effect of the hydroxide of sodium NaOH with pH 12,3 during cycles of minimum contact of 4 am.
Then neutralization of the effluent chemically active ( pH12,3 ) by injection of acid to restore a pH from 6,5 to 7,5 ( neutral pH) before discharge in the city network.
The processing capacity is about 1400 liters in every batch (4 hours), but it is possible to handle less effluent by acting on the pears of levels.
Included: one Sleep off buffer of reception in PEHD with 1 hermetic lid, 1 entrance for the effluent and 1 surverse top communicating with the treatment, 2 Pumps of lifting, 1 agitator, 3 pears of levels and 1 vent outing of a coal-based filter - One Treatment tank in PEHD with 1 hermetic lid, 1 entrance for the effluent and 1 surverse top, 2 Pumps of lifting, 1 agitator, 3 pears of levels and 1 vent equipped with a coal-based filter.
- 1 Unity of correction of pH and indicator of temperature Managed by an Automaton of regulation of pH.
- 1 Pump of injection of soda and acid.
- 2 Containers acid and base
- 1 electric Cupboard Commanding the processing plant.
Photo: tanks of 2000 liters useful for the tank buffer and the treatment tank, for the treatment of a table of autopsy and a table of dissection